PlanaRN tanks for wastewater and drinking water
Reservoirs PlanaRN are designed for the accumulation, averaging and storage of aqueous media.
Capacity 5…120 m3.
Execution is horizontal, cylindrical.
Mounting method — recessed or ground.
Depending on the technical requirements, the PlanaRN tank is designed for underground or surface mounting. Wastewater tanks are equipped with external fins, which significantly reduces the likelihood of corrosion of the internal, working surfaces of the tank when storing such aggressive media as household and septic drains.
* Example of a layout solution for an untreated wastewater averaging tank
If necessary, the tanks PlanaRN are equipped with pumping equipment for pressure discharge of the stored water medium. Pumps with a cutting mechanism are used for household drains. If necessary, the tanks are equipped with a sediment stirring system.
Additional skimmer for collecting floating petroleum products
|Structural design||Block, maximum factory readiness|
|Climatic version||UHL, HL1|
|Equipment and instrumentation design||General Industrial / Explosion-proof (Ex)|
|Tank wall material||Steel 09G2S, stainless steel|
|Tank design||Cylindrical, single- or double-walled|
|Insulation and heating of the tank||Electric or heat carrier of the Customer|
|Anticorrosive coatings||Zinc-filled/polyurethane/epoxy composition|
|Technological pipelines||Stainless steel|
|Garbage collection||Lifting basket-grid|
|Pumping equipment||Submersible pumps with automatic pipe coupling|
|Lifting equipment||Chain hoist or mobile lifting device|
|Automation||LSU based on a programmable logic controller|
|Level sensors||Float detectors / radar level gauge|
|Interfaces with the Customer’s automated control system||RS 485 / Modbus RTU / Ethernet / Modbus TCP|
|Material of the main structures of the BKU||Steel 09G2S|
|BKU enclosing structures||Three-layer sandwich panels 150…250 mm|
The equipment complies with the requirements of TR CU 010/2011 «On the safety of machinery and equipment», TR CU 012/2011 «On the safety of equipment for work in explosive environments» (for explosion-proof equipment).